40MVC / 38MVC. 40MVQ / 38MVQ. Service Manual. HighWall Duct Free Split System. Sizes To TABLE OF CONTENTS. PAGE. SAFETY. View and Download Carrier 40MVC product data online. High-Wall Duct Free Split System. 40MVC Air Conditioner pdf manual download. Also for: 38mvc. Manuals and User Guides for CARRIER 40MVC. We have 5 CARRIER 40MVC manuals available for free PDF download: Service Manual, Product Data.
|Published (Last):||23 March 2006|
|PDF File Size:||10.61 Mb|
|ePub File Size:||14.2 Mb|
|Price:||Free* [*Free Regsitration Required]|
By pressing ‘print’ button you will print only current page. Floor console ductless split system sizes 09 to 12 26 pages.
All connections between indoor and outdoor units must be as shown. Don’t show me this message again.
Carrier 40MVC Installation Instructions Manual
The fan coil is mounted on the wall, near the ceiling. These compact indoor fan coil units take up very little space in the. The mounting plate should be located horizontally and level Indoor Unit on the wall.
High-wall ductless split system sizes to 40 pages. Check with your Carrier representative to obtain Bend tubing with bending tools to avoid kinks and flat spots.
Make sure that the drain tube slopes downward along its en- tire length. This manual also for: The ideal compliment to your ducted system when it is impractical.
Carrier 40MVC Product Data
Conceal the tubing where possible. If unit is exposed to strong winds it is drainage cannot be provided, unit should be equipped with recommended that a wind baffle be used. Table of Contents Add to my manuals Add. Fins shall be bonded to the tubes by mechanical seasonal energy efficiency ratio of 13 at ARI conditions, and a expansion.
Run interconnecting piping and wiring from outdoor unit to indoor unit. Read the entire instruction manual before starting the.
Remove field wiring cover from unit by loosening screws. Carefully remove the mounting plate, which is attached to the back of the indoor unit. Safety Considerations Installing, starting up, and servicing air- -conditioning equipment These instructions cover the installation, start- -up and servicing of can be hazardous due to system pressures, electrical components, 38MVC,MVQ outdoor and 40MVC, MVQ indoor units duct free and equipment location roofs, elevated structures, csrrier.
This manual also for: The connections are sensitive to polarity. Enter text from picture: Page of 14 Go. Add- -ons to current space an office or family room.
Carrier 40MVC Manuals
The red light under dif has come on and the unit will not work. Ideal installation locations include: Don’t have an account? Enter text from picture: To print the manual completely, please, download it.
High-wall ductless split system sizes to 40 pages. Floor console ductless split system sizes 09 to 12 26 pages.
Don’t have an account? When adding air conditioning to spaces that are heated. The deep vacuum method is the most positive way of carrrier a system is free of air and Failure to follow this caution may result in equipment liquid water.